Chiefs Regulation 4
Testing of Fire Protection Equipment
The Los Angeles Fire Department is pleased to offer guidance for your testing of Fire Protection Equipment in accordance with Chief's Regulation Number 4.
- List of Currently Certified Chief's Regulation 4 Testers
- Automatic Closing Fire Assemblies Testers
- Automatic Elevator (Phase I & II) Testers
- Automatic Sprinkler Testers
- Basic Fire Life Safety Systems Only Testers
- Basic and Complex Fire Life Safety Systems Testers
- Battery Systems Only Testers
- Central Station Testers
- Class I Standpipe Testers
- Class II Standpipe Testers
- Class III Standpipe Testers
- Combined Standpipe Testers
- Elevator Witness Only Testers
- Emergency Generator and Battery Systems Testers
- Fire Escape Assemblies Testers
- Fire Pumps Testers
- Gas Detection Tests
- Mechanical Smoke Proof Enclosures Testers
- Pressurized Stairshaft Testers
- Smoke Evacuation Testers
- Highrise Life/Safety Consultant List
- Healthcare Facility Instructor Consultant List
- Study Materials
- The Compliance Engine (TCE)
What We Will Need You To Do! Regulations No. 4 prospective applicant letter
It is important that you first identify:
- Which Fire Protection Systems are in your building.
- The date that each system was last tested.
- The testing frequency required for such systems, are outlined below.
Basic Fire Warning Systems - 1 year
Complex Fire Warning Systems - 1 year
Central Station Signaling Systems - 1 year
Smoke Management Systems - 1 year
Elevators, Automatic - 1 year
Emergency Generator and Lighting Systems
All Occupancies - 1 year
Fire Doors: All Types/All Occupancies - 1 year
Fire Escapes - 1 year
Class I Standpipe Systems - 5 years
Class II Standpipe Systems - 5 years
Class III Standpipe Systems - 5 years
Combined Standpipe Systems - 5 years
Class H Standpipe Systems - 5 years
Fire Pumps - 1 year
Automatic Fire Sprinkler Systems - 5 years
Note: Pre-action, Deluge and Dry Pipe Systems are tested annually.
- Pressure Reducing Valves (PRV's)
- Partial Flow - 1 year
- Full Flow - 5 years
What Is The Process?
If a Chief's Regulation No. 4 test is required, please contact a certified tester to schedule and perform your test.
- The certified tester must submit the test results on Fire Department approved forms, electronically through the compliance engine at http://www.thecomplianceengine.com within 7 days.
- Repair and Retest: If defects are found in equipment that is being tested, correction on such defects shall commence forthwith and shall be completed as soon as possible, but in every case within 30 days of the initial test. At the completion of such repair, the system or device shall be retested as necessary to determine that it is fully operable.
WHO DO YOU NEED TO CONTACT?
- LAFD Bureau of Fire Prevention & Public Safety, Chief's Regulation No. 4 Unit
- Your Neighborhood Fire Station Fire Station NON-Emergency Business Phone Numbers
- The following list of Fire Prevention Bureau (FPB) email addresses can be used for:
- Contacting a Unit about an issue with an FPB occupancy
- General correspondence with a specific Unit
Brush Unit: email@example.com
Central Industrial Unit: firstname.lastname@example.org
Chief’s Reg. 4 Unit: email@example.com
Environmental Unit: firstname.lastname@example.org
Film Unit: email@example.com
Harbor Industrial Unit: firstname.lastname@example.org
High Rise Unit: email@example.com
Hydrants and Access Unit: firstname.lastname@example.org
Legal Unit: email@example.com
Public Assemblage Unit: firstname.lastname@example.org
Schools/Churches/Institutions Unit: email@example.com
Valley Industrial Unit: firstname.lastname@example.org
Valley Public Safety Unit: email@example.com
West Industrial Unit: firstname.lastname@example.org
For Additional Information Contact:
Los Angeles Fire Department
Bureau of Fire Prevention & Public Safety Chief's Regulation No. 4 Unit
200 North Main Street, Room 1700
Los Angeles, CA 90012 USA
Phone: (213) 978-3596